Sulfur or “rotten-egg” odors can develop in water heaters and in corroded iron piping even if the water is chlorinated city water. This usually occurs if the water has a low chlorine residual, high levels of sulfates, and/or the water has sat inactive for days or weeks.
Odors Are Often Caused by Bacteria
The incidence of rotten egg odor or black water in water lines is due to the reaction of sulfates and microorganisms in the water, this can cause hot water tank or water heater smells. To determine the source of the smell, it is important to check to see whether the cold water contains odor or just the hot water.
Run the hot water to notice the odor. Then move to another faucet and run the cold water. If the cold water has an odor, then the source is in the cold water. If the hot water alone has an odor, then the odor is occurring primarily in the water heater, and is why you have hot water smells. A water heater odor killer will help in this situation.
City water is usually chlorinated, which kills odor-causing bacteria. However, in some cases, the chlorine residual may be very low, particularly if your house is at the end of the distribution system and far away from where the chlorine is first injected at the water treatment plant. If you run your cold water and notice an odor, it's best to call your local water utility and report the problem.
Even though the water entering a pipeline from the city water treatment plant can be free of odor, the water may develop odors directly in the distribution line. This can be caused by old iron distribution systems that provide an environment for the sulfate bacteria to grow. Increased bacterial growth depletes both the oxygen and the chlorine residual in the piping. By the time it reaches the house it can be free of chlorine residual and odors can easily develop.
Odors can develop even in cold water piping in the home, especially in galvanized iron piping. Often iron piping in the house is of older age and can be corroded, providing a good environment for the bacteria to grow and odors to develop. If there is an odor in the cold water, and the source is chlorinated city water, it is best to trace and see if the piping is iron piping, and then replace it with copper.
As the first step to this process, you can add hydrogen peroxide or chlorine bleach to the piping and sanitize it. If the smelly water returns, it may be necessary to replace the old galvanized iron pipe with copper piping.
(If you want to read more about water heater odors, check this post out)
Water Heater Odors
Most odors reported on city water are from water heater smells. If your hot water has sulfur or ‘rotten egg' odor to it, the odor is being produced right in the water heater. To remove the smell from the water tank or when hot water heater smells like sulfur, consider sanitizing the tank using hydrogen peroxide.
Almost all water heaters have “anode rods” which in a cathode-anode reaction, produce excess ions that wear off the anode rod and adhere to the inside glass lining of the heater, preventing corrosion. The greater the activity of the anode, the greater the amount of hydrogen ion and hydrogen sulfide gas. If the cold water does not contain odors, but the hot water smells bad, then a thorough sanitizing of the water heater tank with 1 to 2 pints of store-bought hydrogen peroxide will eliminate the odor and smell from the water heater.
See the procedure below. If you are not familiar with the functions of your water heater, DO NOT ATTEMPT this yourself. You can have this done by a licensed plumber to avoid damage to your water heater, or causing electrical problems, or gas explosions by improperly restarting the water heater if gas. We offer this information as informational and educational only, and no warranty or guarantees are expressed or implied. If the water heater is old and corroded, cleaning the sediment from the water and sanitizing by chlorination could cause the water heater to leak.
Procedure for Sanitizing of Hot Water Heater: How to put Hydrogen Peroxide into Water Heater
1. Turn off the manual switch if the water heater is electric. For gas heaters, turn the control to Pilot. Make sure the pilot is still lit so you can restart the water heater when the procedure is completed.
2. Close the cold water inlet valve at the water heater.
3. Open a nearby hot water faucet and the T&P (temperature and pressure valve, located on the top of the water heater) valve to relieve tank pressure. Note of caution: T&P valves may need replacing if defective or old.
4. Drain the water of enough water to compensate for the hydrogen peroxide to be added. Use a hose connected to the drain valve if an open drain is not adjacent to the water heater. Tip: have on hand a hose bib cap, available at any hardware store. When the procedure is completed, in some cases the drain valve will leak, and a hose bib cap can be screwed on the end of the drain valve, preventing the need for a drain valve replacement. Or replace the valve if desired with a new drain valve.
5. Remove the T&P (temperature and pressure relief) valve, anode rod, or disconnect the hot water outlet pipe from the water heater. (ALTERNATE EASY METHOD: Use Water Heater Odor Killer kit)
6. For best results and to preserve the life of your heater, inspect the anode rod. If corroded, replace it with a new aluminum/zinc anode rod, which will create fewer odors. Figure 3 Typical gas water heater cut-away showing anode rod and cold water dip tube.
7. Add 1 to 2 pints of 3% hydrogen peroxide (the kind typically found at drugstores) for every 40 gallons of water heater tank capacity. This can be done by pouring the peroxide into the water heater's outlet pipe opening or into the T&P valve opening; alternatively, you can use the pre-filter screen method (seen here). Re-pipe the water heater and close the T&P valve.
8. Open the cold-water inlet at the heater and fill the tank with water. Observe the water level through the closest hot water faucet. Close the inlet valve when the tank is full.
9. Leave the peroxide mixture in the heater for 1 to 3 hours.
10. After a few hours, open the cold valve again, open all the hot water faucets and allow the peroxide mixture to clean the hot water supply pipes. Drain the remaining peroxide solution from the tank through the heater drain valve.
11. Close the heater drain valve, and completely fill the tank with freshwater. Leave the water in the tank for 15 minutes.
12. After 15 minutes, purge the hot water supply lines and drain the water from the tank through the heater drain valve, flushing out any sediment if present. Close the drain valve.
13. Make sure you purge all air from hot water lines from the open hot water faucets. Close the hot water faucet after all the air is out of the system.
14. Check for water leaks at all fittings used; repair as necessary.
15. Turn on the manual electrical switch, or turn the gas control knob back to “On” and verify that the heater burners have lit and turned back on.
16. Check for the normal heater operation.
If the Odor Returns to the Hot Water
After this procedure is completed, the odor will be eliminated in almost all cases. However, if it returns within a few weeks, then the sanitizing procedure can be repeated. However, in many cases, the cold water will still have problems with recurring odors due to the continued presence of sulfate bacteria and low chlorine residuals in the water.
Other options for smelly, stinky sulfur odors in the water heater are:
1. Remove the standard magnesium anode rod and replace it with an aluminum or zinc anode rod if you haven't already.
2. Replace the water heater with a plastic-lined water heater, or an instantaneous water heater, or a commercial stainless steel water heater (none of which have anode rods).
More Questions? You can always email our technical support department at [email protected] or call us for help at 1-888-600-5426!